Presenter: Jim Meyer
Jim E. Meyer, P.E., has over 45 years of experience in refining petrochemical, chemical, power generation and industrial facilities. He is a principal engineer at CDM Smith, a full service engineering and architectural firm, located in Wadsworth Ohio….More
2KG Training have partnered with ASME in New York for our first live virtual course, to be presented by Jim Meyer. Jim is currently Chair of the ASME B31 Standards Committee and has co-authored chapters on B31.3 Code in the ASME Boiler and Pressure Vessel Companion Guide. He is currently the most sought after ASME B31.3 trainer worldwide and you should not miss this opportunity to learn from his vast wealth of knowledge.
ASME has been defining piping safety since 1922.ASME B31.3 contains requirements for piping typically found in petroleum refineries; chemical, pharmaceutical, textile, paper, semiconductor, and cryogenic plants; and related processing plants and terminals. It covers materials and components, design, fabrication, assembly, erection, examination, inspection, and testing of piping.
This Code applies to piping for all fluids including:
(1) raw, intermediate, and finished chemicals;
(2) petroleum products;
(3) gas, steam, air and water;
(4) fluidized solids;
(5) refrigerants; and
(6) cryogenic fluids.
Also included is piping that interconnects pieces or stages within a packaged equipment assembly.
Key changes to this revision include:
Added specific permission for the owner to designate a representative to carry out selected
responsibilities required by this Code, and noted that the owner retains ultimate responsibility for the actions of the representatives.
Added the ASME B&PV Code Section VIII, Division 2, para. 4.16 flange calculation method as an acceptable way to design flanges for B31.3 applications. The Division 2 procedure considers pressure, gasket seating, and externally applied axial forces and net-section bending moments.
Stress Intensification and Flexibility Factors
Added specific references to ASME B31J-2017 as a resource for stress intensification and flexibility factors as an alternate to Appendix D.
High Cycle Fatigue
Added Appendix W, which describes an alternate method for evaluating high cycle fatigue when specified by the owner. The method in intended to be used when the number of significant stress cycles exceed 100,000.
A significant stress cycle is defined as a cycle with a computed stress range greater than 20.7 MPa (3.0 ksi) for ferritic and austenitic steels. For other materials. or corrosive environments, all cycles shall be considered significant unless otherwise documented in the engineering design. The existing rules provide an acceptable method of evaluating piping systems for fatigue when the number of significant stress cycles is less than or equal to 100,000. The piping cyclic loadings may be due to thermal expansion, anchor motion, vibration, inertial loads, wave motion or other sources.
Heat Treatment for Attachment Welds
Added explicit language requiring heat treatment for structural attachments welded directly to pressure-containing materials when the piping is required to be heat treated.
Added a definition for readily-accessible: those surfaces that can be examined from not more than 600 mm (24 in.) and at an angle not less than 30 degrees to the surface to be examined.
Increased visual examination required for normal fluid service welds from 5% random to 100%.
High Pressure Piping Fatigue Analysis
A fatigue analysis is required for all piping systems in Chapter IX High Pressure Fluid Service. In previous editions, this analysis was permitted to be performed in accordance with the BPV Code, Section VIII, Division 2 or Division 3. Division 2’s fatigue analysis involves using a standard S/N curve to determine the design fatigue life.
Division 3 also allows an S/N curve approach, but only if it can be shown that the piping component will fail in a leak-before-burst mode. Otherwise, a more rigorous fracture mechanics evaluation is required. The Division 3 S/N analysis contains several requirements that are not included in Division 2, such as surface finish and mean stress corrections.. Because the Division 2 approach is less precise than the Division 3 approach, wherever possible, Division 2 was eliminated as an option for the required Chapter IX fatigue analysis.
B31.3 is one of ASME’s most requested codes. It serves as a companion to ASME’s B31.1 Code on Power Piping as well as to the other codes in ASME’s B31 series. Together, they remain essential references for anyone engaged with piping.
Careful application of these B31 codes will help users to comply with applicable regulations within their jurisdictions, while achieving the operational, cost and safety benefits to be gained from the many industry best-practices detailed within these volumes.
Who Should Attend
Intended for manufacturers, users, constructors, designers, and others concerned with the design, fabrication, assembly, erection, examination, inspection, and testing of piping, plus all potential governing entities.
For volume discounts and in-house rates, please contact:
Phindi Mbedzi at 2KG Training
Tel: +27 (0) 11 325 0686
Cell: +27 (0) 71 125 6188